Download the Low Bay Ruggedized Micro Sensor, Installation Guide PDF: English rev.01
The Low Bay Ruggedized Micro Sensor, 8-pin, is designed for outdoor applications, parking structures, and damp or wet locations that require a sensor with an IP65 rating. The sensor can be easily mounted into lighting fixtures or standard 1/2" EMT threaded couplers and fittings such that only the discreet faceplate is visible. The sensor threads into an industry standard ½"-13 threaded mounting hole.
The following sections describe installing the Low Bay Ruggedized Micro sensor, 8-pin, in a fixture or sheet.
- Fixture Mount Sensor Installation
- Sheet Metal Sensor Installation
- Connecting the Sensor Cable to the Control Unit
- Low Bay Ruggedized Micro Sensor (SU-5E-LR)
- Enlighted Sensor Cable
- Enlighted Control Unit
Tools you will Need
- Locknut (Optional)
- Flat blade screwdriver
Caution: Installation and maintenance must be performed by a qualified electrician in accordance with local, state, and national electrical codes (NEC) and requirements.
DO NOT mount the sensor if the mounting accessory has the following defects:
- The knockout hole has a ridge inside that prevents the sensor from going all the way
- The mounting accessory faceplate does not have a large flat surface area for the sensor to fit snugly mounted.
- The sensor lens protrudes out and does not fit securely into the knockout hole.
- A gap exists between the washer and the surface of the mounting accessory.
WARNING: When the sensors are installed incorrectly, it can cause water leakage, electrical shock, and the unit to fail.
Before proceeding with the sensor installation, make sure to de-energize the luminaire.
Note: The black bezel will be attached with the O-ring in place when you receive it. When using the white bezel, make sure that the O-ring is in place under the bezel.
Fixture Mount Sensor Installation
Step 1: Identify an outdoor fixture that has an industry-standard ½” (12.7 mm) -13 threaded mounting hole to which the sensor is to be mounted.
Step 2: Insert the sensor through the mounting hole and thread the sensor until the washer makes contact with the fixture surface.
Step 3: Continue to tighten the sensor with a ¼ turn to make sure that the sensor fits in snugly to prevent water leakage.
Sheet Metal Sensor Installation
Note: For sheet metal mounting, the ½” Lock nut must be ordered separately.
Step 1: Drill a 7/8" (22mm) knock-out hole in the sheet metal.
Step 2: Insert the sensor through the knock-out hole with the lens facing down.
Step 3: Thread the locknut tightly from behind the sheet metal to secure the sensor to prevent water leakage.
Connecting the Sensor Cable to the Control Unit
Step 1: Connect one end of the sensor cable to the Control Unit (CU). For wiring connections from the Control Unit to the sensor, refer to the Control Unit Installation Guide.
Step 2: Energize the luminaire and confirm that the green LED is on solid.
|LED not on||Power issue or faulty sensor. Check power and wiring.|
|Blinking Green||The commissioned sensor has powered up and has detected motion. If there is no motion in the sensor’s field of view, the blinking will stop. Wave your hands below the sensor to restart LED blinking.|
|Solid Green||The un-commissioned sensor has powered up successfully and passed the wiring test –waiting for discovery.|
|Blinking Red||The un-commissioned sensor has powered up and detected a wiring test issue. Check the wiring.|
|Solid Red||Faulty sensor –replace the sensor.|
|Solid Blue||The Sensor received a request to identify itself.|
|Blinking Blue||The un-commissioned sensor was not able to detect an energy measurement device (Control Unit or Driver).|
Model No. SU-5E-LR
Product Code: SU-5e-xxx
FCC ID: AQQ-SU5E