The Enlighted Gateway is the intermediary device between Enlighted Manage and Enlighted Control network.
Refer to the Gateway Installation Guide for installing the Gateway.
The Gateway product, GW-2-01 is not to be mounted outdoors. The Gateway device must be installed indoors. Please note the Gateway is rated for 0 - 50°C. A watertight enclosure does little to ensure the Gateway operates within the stated temperature requirement.
For outdoor installations the Gateway must be mounted indoors and remote the antenna. Suppose an application is required for outdoor sensors, in that case, the Gateway should be mounted on an interior wall and via cable connected to any outdoor omni-directional antenna with a gain of up to 11dBi or less can be used.
For more information, refer to the Gateway Outdoor Antenna Selection Guidelines. Note that Enlighted does not supply the remote antenna components and that the Installation contractor needs to specify, supply and install these items as part of their Scope of Work.
Only Enlighted registered partners and customers have access to download and upgrade firmware images on a Gateway. Refer to the list of available Gateway Firmware Images.