Allows you to manually override the fixture or sensor profile settings and dim the light in the fixture to an absolute level for a period of time in minutes.
|em_ip_address or hostname||The Enlighted Manage (EM) IP address or hostname|
|fixture_id||The Fixture or sensor identifier. Use the Fixture ID returned in the Get Sensor Details by Floor or in EM, select Facility > Floor in the left panel, Floor Plan tab, and double-click the fixture icon in the floor plan to obtain the Fixture ID.|
|mode||Set mode option
abs – Sets the mode to absolute light level dimming
|amount||The percentage ranges from 0-100% light levels (must be a whole number)
|time||The manual override duration time (must be a whole number). The default time is set to 60 minutes.|
0 – Light dimmed successfully
Manually override the sensor profile settings and dim the light to 50% for the fixture with ID ‘27’ for a period of 60 minutes. The status shows that the fixture light was set to dim successfully.