The Enlighted Ruggedized Sensor, 8-pin, is designed for outdoor applications, parking structures, and damp or wet locations that require a sensor with an IP65 rating. The Ruggedized Sensor installs into a standard 1/2 inch fixture knockout. A permanently attached 22-inch cable with an RJ-45 connector must be fed through the opening before the sensor is secured via a threaded locknut provided with the sensor.
Ruggedized Sensor (Front and Rear)
If you have ordered the Hard Ceiling Mount Carrier (HCMC-SU-5E) as an optional component to install the Ruggedized sensor, refer to the following articles:
The following components are shipped with the Ruggedized sensor.
- Enlighted Ruggedized Sensor, 8-pin: SU-5S-HRW/LRW
- ½ inch Lock Nut
- ½ inch LB Conduit Body
- ½ inch Chase Nipple
- Enlighted Control Unit: CU-4E-FM/FMH
- Enlighted Sensor Cable:
- Cable Coupler: CPL-RJ45
- Hard Ceiling Mount Carrier: HCMC-SU-5E
Tools you may Need
- ½ inch Knock out tool
A qualified electrician must perform installation and maintenance per local, state, and national electrical codes (NEC) and requirements.
The Ruggedized sensor, 8-pin, is shipped with the cable attached to the sensor. The sensor can be mounted to the fixture using a conduit body and chase nipple or locknut.
Step 1: De-energize the luminaire.
Mounting using the Conduit Body and Chase Nipple
Step 1: Remove the cover plate of the ½ inch LB conduit body by removing the two screws.
Step 2: Thread the Ruggedized sensor onto the LB conduit body.
Step 3: Replace the cover and two screws on the LB conduit body.
Step 4: Knock out a ½ inch hole on the end of the light fixture.
Step 5: Mount the Ruggedized Sensor LB Conduit to the fixture by guiding the sensor cable through the knockout and chase nipple into the fixture.
Step 6: Thread the chase nipple to connect the LB conduit to the fixture securely.
Mounting using the Locknut
Step 1: Knock out a ½ inch hole on the bottom of the light fixture.
Step 2: Glide the sensor cable through the knockout of the fixture.
Step 3: Thread the locknut tightly to secure the sensor to the fixture.
Connecting the Sensor Cable to the Control Unit
Step 1: Use an RJ45 coupler with an Enlighted Sensor cable to connect the RJ45 end of the sensor cable to the Control Unit's connector (CU).
For wiring connections from the Control Unit to the sensor, refer to the Control Unit Installation Guide.
Step 2: Energize the luminaire and confirm that the green LED is solid.
|LED not on||Power issue or faulty sensor. Check power and wiring.|
|Blinking Green||The commissioned sensor has powered up and has detected motion. If there is no motion in the sensor’s field of view, the blinking will stop. Wave your hands below the sensor to restart LED blinking.|
|Solid Green||The un-commissioned sensor has powered up successfully and passed the wiring test –waiting for discovery.|
|Blinking Red||The un-commissioned sensor has powered up and detected a wiring test issue. Check the wiring.|
|Solid Red||Faulty sensor –replace the sensor.|
|Solid Blue||The sensor received a request to identify itself.|
|Blinking Blue||The un-commissioned sensor was not able to detect an energy measurement device (Control Unit or Driver).|
SU-5S-HRW: High Bay, White, Ruggedized Sensor
SU-5S-LRW: Standard Bay, White, Ruggedized Sensor
xRx: HRW, LRW
xxx: IoT Node (IoT), Connected Lighting (CL), Independent Lighting/Enlighted One (IL)
FCC ID: AQQ-SU5S
- Ruggedized Sensor, 8-pin, (SU-5S-xRx) Spec Sheet
- Hard Ceiling Mount Carrier (HCMC-SU-5E) Spec Sheet
- Hard Ceiling Mount for Diffuser Fixture Mount