Download the Manage Riser diagram for Enlighted Fixture Mount Micro Sensor - KIT-SU-5E-D.
This article shows the placement of Enlighted Fixture Mount Micro Sensor - KIT-SU-5E-D with control units, gateways, switches, and Manage.
The maximum CAT5e or CAT6 cable distance between Gateway and PoE switch or PoE switch to PoE switch is 300' and installation FBO, per IEEE 802.3 Standards.
One dedicated 20A, 120v circuit with the duplex receptacle, recommended for each 8-port PoE switch and Enterprise Energy Manage.
Fixtures with integrated Enlighted sensors and control units communicate wirelessly with the Enlighted Gateway.
Groups of fixtures controlled by an Enlighted (2-wire) sensor unit and communicate wirelessly with the Enlighted gateway.
Enlighted Room Controllers (Wall Switch - WS-2-00) communicate wirelessly with Enlighted sensors that are on the same radio channel (gateway).
Enlighted devices and wiring must be installed in accordance with state, local, and National Electric Codes.
Plug Load Controller communicates wirelessly with the Enlighted Gateway.
Sample devices for the numerical markings in the above riser diagram are listed below:
|1||Sample DALI Downlight group with external PSU|
|2||Sample Troffer with internal PSU SR driver and field mounted external sensor|
|3||Sample Emergency Troffer with internal PSU SR driver|
|4||Sample Troffer with internal PSU SR driver and OEM mounted internal sensor|
|5||Sample Plug Load Controller - ceiling mounted|
|6||Sample Linear Pendant with internal PSU SR driver and OEM mounted internal sensor|
|7||Sample Emergency Linear Pendant with internal PSU SR driver and OEM mounted internal sensor|
|8||Sample Surface Sensor - Desk Mounted|